0061 RF Occupancy Or Vacancy Sensor User Guide Lutron Electronics
Refer to that product’s installation sheet for instructions. Twist and remove mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) devices that routinely management lights by way of RF communication with a dimming or switching device. These Sensors detect the heat from folks shifting inside an space to find out when the area is occupied. The Sensors then transmit the suitable commands to the associated dimming or switching machine to show the lights on or off routinely, offering each convenience and distinctive vitality savings. Sensor doesn't perform satisfactorily from this location, it may be moved to 1.4 Ifanother location by pulling the Sensor straight down and repeating steps 1.3 and 1.4. 1.5 If the Sensor’s efficiency is satisfactory, it ought to be completely hooked up to the ceiling tile, as described in part G. Permanent Mounting. Non permanent Strong Ceiling Mounting Use this process if the Sensor might be mounted on a solid, continuous ceiling surface equivalent to drywall, plaster, concrete, or wooden. Two 3M™ Command™ adhesive strips are offered for briefly mounting and testing the Sensor on smooth, stable ceiling surfaces. These strips are designed for straightforward, damagefree removing and will not be reusable. These strips should not be used for completely mounting the Sensor (see section G. Everlasting Mounting ). Rigorously comply with the removing directions beneath to ensure the ceiling is not damaged throughout elimination. Be aware: Do not use the adhesive strips on ceiling tiles, as they will doubtless cause injury to the tile upon removal. Easy-to-observe Directions Set-Up To ensure that the Sensor to operate correctly, it must first be set up with a corresponding dimming or switching device. The process for organising a Sensor with a Maestro Wireless® (MRF2- solely) Dimmer or Digital Switch is detailed beneath. P/N 041-172a 2.1 Peel the crimson "Command Strips" liner off of one of many adhesive strips and apply the strip to the flat side of the mounting bracket as shown in the diagram. Be aware: Don't cowl the bracket’s screw holes as a result of they are going to be used to mark screw hole areas on the ceiling. Organising a Sensor with a Maestro Wireless Dimmer or Digital Swap Dimmer Key Features · Low Upkeep. 10-12 months battery life. Handy low-battery indicator. · Multiple Gadgets. Up to 3 Sensors can work together to control lights for broader protection in giant spaces. Each Sensor could also be added to as much as 10 receiving units. Sensor Operation Occupancy Model - The Sensor will automatically flip the lights on when the area is occupied and mechanically turn the lights off after the house is vacated. The Sensor will mechanically flip the lights off after the space is vacated. There is a built-in 15-second vacancy grace interval that begins when the lights are routinely turned off, throughout which the lights will mechanically turn again on in response to movement. This grace interval is provided as a security and comfort feature within the occasion that the lights flip off while the room is still occupied, so that the person does not need to manually flip the lights again on. After 15 seconds, the grace interval expires and the lights have to be manually turned on. This Sensor is part of a system and can't be used to regulate a load with no compatible dimming or switching device. Refer to the instruction sheets of the receiving gadget(s) for set up data. The Sensor could also be put in up to 60 ft (18.Three m) away from the related dimming or switching system(s) if they're in direct line of sight. If there are partitions or different obstacles between the Sensor and receiving gadget(s), the Sensor should be situated within 30 ft (9.1 m). Caution: This product must not be used to control gear which could create hazardous conditions, resembling entrapment, if operated accidentally. Sensor in a location where it has a broad view outside the supposed area. If that is unavoidable, the lens may be masked to block the view of undesired areas (discuss with part I. Lens Masking). This warranty is in lieu of all other categorical warranties, and the implied guarantee of merchantability is restricted to 1 year from buy. This guarantee doesn't cowl the cost of set up, elimination or reinstallation, or harm ensuing from misuse, abuse, or harm from improper wiring or installation. This guarantee doesn't cover incidental or consequential damages. LUTRON’S Legal responsibility ON ANY Claim FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Installation, Delivery, OR USE OF THE UNIT SHALL By no means EXCEED THE PURCHASE Worth OF THE UNIT. This guarantee provides you specific authorized rights, and it's possible you'll have other rights which range from state to state. Some states do not allow the exclusion or limitation of incidental or consequential damages, or limitation on how long an implied guarantee may last, so the above limitations may not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst emblem are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American National Requirements Institute. IEC is a trademark of the International Electrotechnical Fee. Made and printed in the U.S.A. 25/09/09 P/N 041-172 Rev. A 8 ft (2.4 m) 18 x 18 ft (5.5 x 5.5 m) 13 ft (4.0 m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.Four m) 10 ft (3.0 m) 22 x 22 ft (6.7 x 6.7 m) sixteen ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.Eight m) Short-term Mounting Methods 1.1 1.2 Insert the ceiling tile mounting wire by the two smaller holes within the mounting bracket and substitute the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs by means of the tile, making sure the Sensor is flush to the tile. Observe: Don't twist wire legs together. 1.2 After the Sensor has been briefly mounted, leave the Sensor in place on the tile and either take the tile down or remove an adjacent tile to gain access to the legs of the mounting wire on the again of the tile. Low Activity: This is probably the most delicate setting and can detect very slight motions. This is the really helpful setting, as it will work properly for almost all functions. It is ideal for spaces the place occupants will typically be seated for long intervals of time. Twist the wire legs together tightly so the mounting bracket remains snug against the tile. This setting is barely less sensitive than the Low Activity setting and can be utilized for areas that experience normal exercise. That is the least delicate setting and can be utilized for areas that can typically only experience massive motions, corresponding to foot traffic. The Low Activity setting is the default and can carry out greatest for many purposes. Not often, if the Sensor is positioned close to external noise sources such as heating vents, air conditioning vents, or mild bulbs, it could turn the lights on with out occupancy or keep the lights on too long after vacancy. If this happens, altering the sensitivity to Medium Activity or High Exercise ought to resolve the problem. Exchange the tile. Everlasting Solid Ceiling Mounting 2.1 2.2 2.3 Advanced Set-Up Operation The advanced set-up is accessed by using the buttons on the again of the Sensor. Drill two 3/16 in (4.6 mm) pilot holes for the provided screw anchors. Press the anchors into the holes and tap flush with a hammer. To display the current setting, press and release the specified button. An LED will illuminate briefly, indicating the present setting. Place the flat aspect of the mounting bracket towards the ceiling and install the two supplied screws using a hand screwdriver. To regulate a setting, press and hold the specified button till the LED corresponding to the current setting begins flashing quickly, indicating the setting can now be adjusted. Every subsequent button press of less than 2 seconds will increment the mode to the following available setting. Urgent any of the other buttons will don't have any effect. To save lots of the chosen setting, press and hold the button until the LED turns on stable, indicating the saved setting. In the course of the adjustment procedure, if there isn't any exercise for 30 seconds, the LEDs will turn off and no settings will probably be saved. Observe: Don't over-tighten. 2.4 Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise course till the Sensor locks into place. To remove the bracket from the ceiling, grasp the elimination tab on the adhesive strip and pull the tab VERY SLOWLY straight throughout the ceiling, stretching the strip till the bracket releases from the ceiling. Discard the strip. By no means pull the strip at an angle, as it may break or injury the ceiling surface. Be aware: Don't pull at an angle. Lens Masking (Elective) Every time potential, the Sensor ought to be installed in a location the place it can not simply see into areas outdoors the meant space, akin to hallways or adjoining rooms. If this example can't be averted, parts of the lens could also be masked with the supplied labels to dam the Sensor’s view of the undesired areas. It's endorsed to remove the Sensor from the mounting bracket before making use of Superior Set-Up (Optional) the masking labels. The Sensor options several advanced set-up modes. For the majority of installations, the default settings will provide the most effective efficiency and you is not going to must utilize the superior set-up. The Occupancy version of the Sensor has three adjustable superior set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Solely model has only two modes (Auto-On not accessible). The default settings are listed below. The Sensor will be screwed onto the mounting bracket in several completely different orientations. Be sure to note the Sensor’s orientation earlier than taking it down and substitute the Sensor in the same orientation to make sure the intended space will get blocked. Outer lens sections correspond to the detection areas furthest away from the Sensor, while interior sections correspond to regions nearer to the Sensor. Be careful when applying the labels to keep away from creating gaps between adjoining masked sections. The Sensor may detect movement by means of inadvertent gaps. All the time (Occupancy version solely) Timeout 30 min 15 min 5 min Auto-On Always Low gentle Disable Activity Timeout 30 min 15 min 5 min Advanced Set-Up Modes Auto-On All the time Low mild Disable Activity Exercise: Low Activity Lens sections shown in white are masked with labels Timeout The Sensor will flip the lights off if no motion happens at some point of the timeout period. There are three out there timeout settings: 5, 15, and half-hour. Lens Mask Lens sections proven in grey have not been masked Auto-On The automated-on functionality of the Sensor will be adjusted to regulate how the lights respond upon initial occupancy. There are three accessible settings: All the time, Low mild, and Disable. All the time: The lights will at all times activate. Testing Sensor Protection With the Sensor mounted on the ceiling, press and release the "Test: Sensor" button on the front of the system. The lens will glow briefly, indicating the check mode has been entered. Word: There is a warm-up interval of roughly 40 seconds after the batteries are put in earlier than the test mode might be activated. If the button is pressed during this time, the lens will flash continuously until the heat-up period is complete, and then the take a look at mode shall be automatically entered. Confirm the protection area by walking by means of the area and observing the lens. The lens will glow stable every time movement is detected. If the lens remains off throughout movement, the Sensor can not detect motion at that location. Press and release the "Test: Sensor" button once more to exit the take a look at mode. If the button isn't pressed, the take a look at mode will mechanically trip quarter-hour after being enabled, or 5 minutes after the final detected motion if the room is vacated. If the Sensor has important bother detecting motion in the course of the check, it needs to be moved to a different location and retested. If the Sensor nonetheless has poor detection from the brand new location, check with the Troubleshooting section. Momentary Drop Ceiling Mounting Use this process if the Sensor will probably be mounted on a ceiling tile. The ceiling tile mounting wire is supplied for each temporary and permanent mounting of the Sensor to drop ceilings composed of a number of tiles. It is designed to permit temporary mounting, testing, and repositioning (if needed) of the Sensor without damaging a ceiling tile. As soon as the Sensor’s remaining place has been chosen, the mounting wire could be twisted to lock the Sensor in place permanently. If the Sensor protection and wireless communication tests have been efficiently accomplished, use the mounting bracket as a template to mark the screw hole areas with a pencil. Observe: Pull very slowly. Max. Room Dimensions Radius of Protection for Full Protection at Floor If you are uncertain about correctly positioning the Sensor, the following temporary mounting and testing procedures are advisable to verify correct performance before permanently putting in the Sensor. Sensor’s detection range is dependent on the ceiling height, as proven in the table below. Discover: Do not disassemble, crush, puncture, or incinerate the batteries. Don't dispose of batteries in normal family waste. Please recycle, take to a correct battery disposal facility, or contact your native waste disposal supplier regarding local restrictions on the disposal or recycling of batteries. O NOT mount the Sensor inside four ft (1.2 m) of HVAC vents or gentle bulbs installed beneath the ceiling line. Warmer rooms may reduce the Sensor’s capability to detect occupants. Use solely excessive-high quality lithium batteries, measurement CR123, three V (ANSI-5018LC, IEC-CR17345). Do not use rechargeable batteries. Using improperly rated batteries might harm the Sensor. For questions concerning the installation or operation of this product, call the Lutron Technical Assist Center. Please present precise model quantity when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Mild Degree (occupancy model, dimming gadgets solely) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach path till the Sensor locks into place. Sensor coverage and wireless communication tests as described in 2.6 Carry out sections E. Testing Sensor Protection and F. Testing Wireless Communication. The Sensor should be put in in a location where it has a superb view of all elements of the room. The Sensor requires line of sight to operate properly. If you can't see the Sensor, it cannot see you. The Sensor can't see through glass objects reminiscent of patio or shower doors. The vary and performance of the RF system is very dependent on quite a lot of complicated elements resembling: · Distance between system parts · Geometry of the building structure · Building of walls separating system components · Electrical tools positioned close to system parts Technical Help 2.2 Identify a location on the ceiling where the Sensor may have a very good view of the room. 2.3 Take away the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use only. Do not install on ceilings greater than 12 ft (3.7 m) or non-ceiling surfaces. Doing so could significantly inhibit the Sensor’s efficiency. 4. Don't paint Sensor. · · · · The "Lights On" and "Lights Off" buttons should now change the lights within the room on and off, respectively, when pressed. Repeat the above process to set up the Sensor with any extra gadgets. The Sensor is intended for indoor use solely. Function between 32 °F and 104 °F (zero °C and forty °C). 1.1 several seconds. Sensor that has been set up. After roughly 6 seconds, the lens will flash rapidly several occasions, indicating the light level has been saved. All Sensors set up with the Dimmer will now use the saved occupancy gentle degree. 2. Clean Sensor with a tender damp cloth only. Don't use any chemical cleaners. Observe: This tools has been tested and located to comply with the bounds for a class B digital machine, pursuant to part 15 of the FCC guidelines. These limits are designed to supply reasonable protection in opposition to harmful interference in a residential set up. This gear generates, uses and might radiate radio frequency power and, if not installed and used in accordance with the directions, could cause harmful interference to radio and tv reception, which could be determined by turning the gear off and on. The user is inspired to attempt to right the interference by a number of of the following measures: Reorient or relocate the receiving antenna. Enhance the separation between the tools and receiver. Connect the equipment into an outlet on a circuit totally different from that to which the receiver is linked. Consult the seller or an experienced radio/Television technician for help. Caution: Modifications or modifications not expressly approved by Lutron Electronics Co. might void the user’s authority to function this tools. This gadget complies with Half 15 of the FCC guidelines. This system should accept any interference received, including interference that will cause undesired operation. Swap 2.1 Set the Dimmer to the specified mild degree for entering the room. 2.2 Save holding the "Lights On" button on the entrance of a Observe: For both Sensor model, the lights can be manually turned off at any time by using the dimming or switching system instantly. Essential Notes or Add the Sensor to the Dimmer or Change by urgent and holding the "Lights Off" button on the front of the Sensor for roughly 6 seconds until the lens flashes briefly. The lights in the room can even flash three occasions, indicating the Sensor has been successfully added. The Dimmer or Switch will exit set-up mode robotically. The sensitivity of the Sensor can be adjusted based mostly on the anticipated stage of activity inside the room. There are three obtainable activity settings: Low Exercise, Medium Exercise, and Excessive Exercise. Permanent Drop Ceiling Mounting Word: Depart the removing tab uncovered past the sting of the bracket so it can be accessed for removal later. 6 seconds till all LEDs on the device start flashing. Launch the tap button. Sensor is detecting movement in areas that are not desirable, comparable to hallways or adjacent rooms, consult with part I. Lens Masking. If Sensor detection is passable during this take a look at, perform the wireless communication test as described in part F. Testing Wireless Communication. Testing Wireless Communication This test must be carried out to confirm that the Sensor has been accurately set up with the corresponding dimming or switching gadget and that there's proper wireless communication from the chosen Sensor location. If the lights in the room are usually not on, flip them ON manually at the dimming or switching device. Press and release the "Lights Off" button on the front of the Sensor. The lights ought to flip OFF. Press and release the "Lights On" button on the entrance of the Sensor. The lights should turn on. If the lights do not reply accurately, seek advice from the Troubleshooting section. Low light: The lights will solely turn on routinely upon entry if there is not already enough ambient gentle within the room. Hallway falls inside Sensor’s coverage area. Disable: This setting converts the Sensor to vacancy mode. The lights is not going to robotically activate but will still robotically flip off after vacancy. The lights should be manually turned on by using the related dimming or switching machine. Notice: The 15-second vacancy grace interval is lively in this mode. Discuss with the Sensor Operation section at the start of this document for more particulars. Troubleshooting Symptom Attainable Causes Resolution Lights do not turn on when space is occupied. Sensor is not accurately added to dimming / switching machine(s). Sensor’s Auto-On setting is about to "Low light" or "Disable". The lights have been just lately turned off manually and the timeout has not but expired. Sensor does not have full view of room. Sensor is outdoors wireless vary of dimming/switching device. Seek advice from section B. Set-Up. Refer to part H. Advanced Set-Up. Dimming/switching gadget has been improperly wired. Gentle bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is just too short for this utility. Sensor doesn't have full view of room. Lens mask is improperly utilized. Sensor’s sensitivity is too low. Sensor’s timeout has not but expired. An external noise source equivalent to an HVAC vent is interfering. Discuss with part A. Pre-Installation. Conduct of lights does not match Sensor settings. Sensor coverage extends beyond room perimeter. The supposed setting was not saved. A number of Sensors are added to a dimming/switching machine and their settings don't match. Check with section A. Pre-Installation. Refer to section C. Sensor Placement or I. Lens Masking. Seek advice from section H. Advanced Set-Up. Discuss with section H. Advanced Set-Up. Sensor lens does not glow in response to movement throughout Sensor protection testing. Sensor can't see motion because of obstruction. Room is just too big or oddly shaped. Move Sensor to another location. Seek advice from section C. Sensor Placement. A number of Sensors could also be obligatory for full room protection. Try moving Sensor to a new location or reducing sensitivity. Check with part C. Sensor Placement or H. Superior Set-Up. Lights turn OFF whereas space is occupied. Lights keep ON after house is vacated. Lens doesn't stop glowing during Sensor protection testing even when there isn't any movement. Lights do not respond accurately during wireless communication testing. Sensor lens flashes and lights don't turn on when space is occupied. Battery has been put in incorrectly. An exterior noise supply corresponding to an HVAC vent is interfering. Check with section C. Sensor Placement. Confer with section C. Sensor Placement or F. Testing Wireless Communication. Check with section H. Advanced Set-Up. Discuss with section C. Sensor Placement. Refer to part I. Lens Masking. Consult with part H. Superior Set-Up. Check with part H. Advanced Set-Up. Strive shifting Sensor to a new location or lowering sensitivity. Check with section C. Sensor Placement or H. Advanced Set-Up. Sensor is not accurately added to dimming / switching system. Sensor is outside wireless vary of dimming/switching gadget. Refer to part B. Set-Up. Move Sensor closer to dimming/switching gadget and retry check. Seek advice from section F. Testing Wireless Communication. Battery has been put in incorrectly. Dimming/switching machine has been improperly wired. Mild bulb(s) burned out. Breaker is off or tripped. Battery is low. Check with part A. Pre-Set up. Take away sensor from take a look at mode. Confer with section E. Testing Sensor Coverage.